Good electrician required in Killiney. No RCBO and no power in Kitchen sockets
Got a call today from a customer in Killiney. They had no power in their electric shower or sockets in the kitchen.
On investigation I discovered they had no RCD on the shower and the sockets and shower were on the MCB. I couldn’t believe that an electrician had done the job.
I installed an RCBO for the shower and a new MCB for the socket circuit.
The customer will have a safer Christmas now.